A fire engineering brief (FEB) process will ensure fire safety designs that do not follow an acceptable solution complies with the building code.
The New Zealand Building Code is performance-based. It states how a building must perform in its intended use rather than describing how the building must be designed and constructed. Compliance with an acceptable solution or verification method is a means for establishing compliance with the building code, but are not the only means.
If your fire safety design does not use an acceptable solution as a means of compliance, then a specific fire engineering analysis is required to establish compliance with the building code using a verification method or an alternative solution.
A fire engineering brief (FEB) process is used to define the scope of work for the fire engineering analysis. This process involves an early discussion between key stakeholders on the project scope, analysis methodologies, design acceptance criteria and any potential regulatory constraints.
As a minimum, the key stakeholders include the fire designer, the peer reviewer, a representative from Fire and Emergency New Zealand (FENZ), a representative from the building consent authority (BCA) and a representative for the property owner. The fire designer and peer reviewer are required to have chartered professional engineer status in fire engineering.
Typically, the draft FEB documentation will have a concept design prepared by a suitably qualified fire engineer. The concept fire design should include plans, details of occupant characteristics, an initial determination of the preferred active and passive fire safety systems, and a list of any challenging matters for discussion.
Fire engineers can refer to the International Fire Engineering Guidelines(external link) or other internationally recognised standards for further information regarding the content of fire engineering brief documentation.
You are required to use a FEB process when:
Download and complete a request for service (Building) [DOCX, 206 KB] application.
We'll review your application and provide comments within approximately 20 working days.
To minimise delays in processing the building consent application, ensure that all key stakeholders have reached an agreement.
It is expected that any significant concerns raised by the BCA, the peer reviewer and the FENZ fire engineer are resolved before fully developing the design. Addressing minor comments may delay processing the building consent application.
The BCA approval will be provided after:
The FEB approval requires the following information to accompany the building consent application:
The fire designer will carry out a design coordination review based on Engineering NZ Practice Note 22. This review is to ensure that the intent of the fire design has been correctly transferred into documentation from other design disciplines.
The design disciplines whose plans and specifications require coordination include; architectural, structural, mechanical, electrical and hydraulic.
On completing the review the fire designer issues a design coordination statement that references the documents reviewed, including their revision number and issue dates.
The documents submitted with the building consent application must be the same versions referenced by the design coordination review statement.